Glossary: Conductive Flooring
When referring to flooring materials, the term “conductive” is often confused with the term “static dissipative.” Floors are correctly classified as conductive or static-dissipative based upon their electrical resistance to ground. Electrical resistance is measured in ohms (Ω).
The resistance to ground of a conductive floor is usually defined as < 1.0 x 10E6 ohms, measured per ANSI/ESD STM 7.1. Conductive flooring meets the required resistive properties (< 10E9 ohms) for a floor complying with the resistance to ground parameter in ANSI/ESD S20.20-2014.
2) A type of flooring intended to prevent, mitigate, dissipate, conduct, remove or ground excessive static electricity charges on people, furniture, mobile carts and equipment.
Note: This generic description is not useful in evaluating static-control flooring materials. Materials should be evaluated based upon their electrical resistance, suitability for the application, and compliance with industry standards.
Learning Center Articles
- 7 Common Mistakes Selecting an ESD floor
- A Guide to ESD Flooring Selection
- Avoid Costly Failures: What You Need to Know When Specifying ESD Flooring
- Choosing ESD Flooring for:
- ESD Footwear: What Is It and When Is It Necessary?
- ESD Footwear for Electronics Manufacturing and Handling Applications
- Facility Managers' Guide to Selecting ESD Flooring
- The Need for Due Diligence in Specifying Static-Free Flooring
- Standard of Care for Specifying Floors in Mission-Critical Spaces
- Understanding the Hidden Costs of ESD Flooring